Cast Your Vote
Connecting Receptacle Grounding Terminal to Box
Let's Go Racing!
Win a Free Road America Race Weekend for Two
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code” and “NEC” refer to the
National Electrical Code®, which is a registered
trademark of the
National Fire Protection Association.
EC&M Product of the Year Competition
Cast Your Vote Now!
Do you want the opportunity to win $100? Then visit the
EC&M Web site by June 22 to
your vote in EC&M's Product of the Year competition and help us
identify the best new product introduced to the electrical industry in
When you visit the EC&M Web
site, an automatic poll will pop up. (Note: If you have a pop-up
blocker program, it may prevent you from seeing the poll. Temporarily
disable the program to allow the poll to appear on your computer.) You
then need to type in your contact information, choose your favorite
product, and click submit. It's that simple. For additional information
on each category winner, click on the product name in the pop-up poll
window and it will bring you to a page that features product summaries
for all 24 category winners.
A panel of seven judges initially narrowed the field from 108
entrants down to 24 category winners, and now we need your help to
determine the Platinum, Gold, and Silver Award winners. The competition
has honored innovation and excellence in product development in the
electrical industry for the past seven years.
Fluke 117 Electrician's Multimeter with
Non-Contact Voltage. Designed by Electricians. Engineered by Fluke.
Compact true-rms meter for commercial applications. The Fluke 117 is
ideal meter for demanding settings like commercial buildings, hospitals
and schools. The 117 includes integrated non-contact voltage detection
to help get the job done faster. For
more information, click here.
Top 50 NEC Rules
Connecting Receptacle Grounding Terminal to Box
By Mike Holt
Receptacles must have their grounding contacts
to an effective ground-fault current path by bonding the receptacle's
grounding terminal to a metal box, unless the receptacle's grounding
terminal is grounded (bonded) to an effective ground-fault current path
by one of the methods provided in (A) through (D). See 406.3 for
The NEC doesn't restrict the position of the receptacle grounding
terminal; it can be up, down, or sideways. All proposals to specify the
mounting position of receptacles have been rejected.
(A) Surface-Mounted Box. Where the box is mounted on the
surface, direct metal-to-metal contact between the device yoke and the
box can serve as the effective ground-fault current path. To ensure an
effective ground-fault current path between the receptacle and metal
box, at least one of the insulating retaining washers on the yoke screw
must be removed.
Receptacles secured to a metal cover [406.4(C)] must have the
receptacle's grounding terminal bonded to the box, unless the box and
cover are listed as providing continuity between the box and the
(B) Self-Grounding Receptacles. Receptacle yokes designed and
listed as self-grounding can be used to establish the effective
ground-fault current path between the device yoke and a metal outlet
box. Note: Outlet boxes cannot be set back more than 1/4-inch
from the finished mounting surface [314.20].
(C) Floor Boxes. Listed floor boxes are permitted to
the bonding path between the device yoke and a grounded (bonded) outlet
(D) Isolated Ground Receptacles. Isolated ground receptacles
have the grounding terminal insulated from its metal mounting yoke.
Therefore, the grounding terminal of an isolated ground receptacle must
be connected to an equipment grounding (bonding) conductor that
the effective ground-fault current path to the power source.
Isolated ground receptacles must be identified by an orange triangle
located on the face of the receptacle [406.2(D)]. Sometimes the entire
receptacle is orange, with the triangle molded into the plastic face in
a color other than orange.
Editor's note: This information was extracted from Mike
the National Electrical Code
One-touch automated design and one-touch automated protective device
coordination options, available in EasyPower 8.0, will be introduced in
the Hands-On training in Indianapolis, Indiana on September 17-21,
2007! Streamline the implementation of your Arc Flash and
Electrical Safety Program. What used to take hours, now takes mere
seconds! EasyPower delivers Windows® -based tools for
designing, analyzing, and monitoring electrical power systems.
What's Wrong Here?
By Joe Tedesco
Think you know how this installation violates the
NEC? Visit EC&M's
Web site to see the answer.
Hint: Don't overlook the obvious on this one
By Mike Holt
Q. When a lighting and appliance panelboard is
fed from the secondary of a 3-phase transformer, is the panelboard
required to have a main breaker installed in it?
Visit EC&M's Web
site to see the answer.
By Steven Owen
Q. When installing a high-impedance grounded
neutral system for a 480V, 3-phase electrical system, the following
question arises. Where is the proper location for the grounding
- Between the equipment bonding jumper and the system neutral.
- Between the main bonding jumper and the system neutral.
- Between the transformer secondary and the first disconnecting
- Between the grounding electrode conductor and the system
Web site for the answer and explanation.
Cool Electronic Cabinets
Beat the summer time heat and prevent hot weather failures. UL Listed
Cabinet Coolers from EXAIR produce 20 degree Fahrenheit air from an
ordinary supply of compressed air to cool electrical controls.
Thermostat control minimizes air usage. Maintains the NEMA 4, 4X
(stainless steel) and 12 rating of the enclosure. Web site offers
detailed information, downloadable drawings and PDF literature.
Shows and Events
Let's Go Racing! Win a Free Road
America Race Weekend for Two
EC&M magazine and Generac Power Systems have
teamed up to offer an expenses-paid weekend (August 10-12, 2007)
featuring two of the world's fastest racing series. The third annual
Generac Power Weekend is one thrilling day of American LeMans series
racing (the Generac 500) and an equally exciting day of Champ Car
at its finest (the Generac Grand Prix). It's your chance to see both
series compete in a single weekend at one of North America's most
beautiful tracks. Located in the hilly heart of Wisconsin's scenic
Kettle Moraine area, Road America is a four-mile permanent road course
that tests drivers with 14 challenging turns.
Enter by July 10, 2007. Visit the Generac Power Systems virtual
at the EC&M
E-Tradeshow. Full contest rules are available online in the Generac
E-Tradeshow booth. For more information about the Generac Power
go to www.roadamerica.com.
EC&M Code Change
Where do you turn when you need accurate information on
changes to the National Electrical Code? Acknowledged as the leaders in
providing information on the NEC, EC&M magazine and EC&M
Seminars have been the preferred sources of this information for more
than 60 years. Seven Code change conferences have been scheduled in the
fall of 2007. Host cities include: Atlanta, Boston, Dallas, Orlando,
Philadelphia, St. Louis, and Seattle.
As an approved provider with the National Council of Examiners for
Engineering and Surveying (NCEES), through its Registered Continuing
Education provider Program (RCEPP), professional engineers attending
of our 2008 Code change conferences will receive Professional
Development Hours (PDHs), a requirement for re-licensing in many
The conferences are also approved by every state that has a continuing
education requirement for contractors and electricians.
For additional information on the dates and locations of these
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2014, Penton. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.