Induced Currents in Metal Parts
Comments Sought on
Tentative Interim Amendments
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code” and “NEC” refer to the
National Electrical Code®, which is a registered
trademark of the
National Fire Protection Association.
Top 50 NEC Rules
Induced Currents in Metal Parts
By Mike Holt
To minimize induction heating of ferrous metallic
raceways and enclosures -- and to maintain an effective ground-fault
current path -- all conductors of a circuit must be installed in the
same raceway, cable, trench, cord, or cable tray. See 250.102(E),
300.3(B), 300.5(I), and 392.8(D).
When alternating current (AC) flows through a conductor, a pulsating
or varying magnetic field is created around the conductor. This
field is constantly expanding and contracting with the amplitude of the
AC current. In the United States, the frequency is 60 cycles per
Since AC reverses polarity 120 times per second, the magnetic field
surrounds the conductor also reverses its direction 120 times per
second. This expanding and collapsing magnetic field induces eddy
currents in the ferrous metal parts that surround the conductors,
causing the metal parts to heat up from hysteresis.
Hysteresis heating affects only the ferrous metals with magnetic
properties, such as steel and iron, but not aluminum. Simply put, the
molecules of steel and iron align to the polarity of the magnetic field
and when the magnetic field reverses, the molecules reverse their
polarity as well. This back and forth alignment of the molecules heats
up the metal -- the greater the current flow, the greater the heat
rise in the ferrous metal parts.
When conductors of the same circuit are grouped together, the
magnetic fields of the different conductors tend to cancel each other
out, resulting in a reduced magnetic field around the conductors. The
lower magnetic field reduces induced currents in the ferrous metal
raceways or enclosures, which reduces hysteresis heating of the
surrounding metal enclosure.
When single conductors are installed in nonmetallic raceways as
permitted in 300.5(I) Ex. 2, the inductive heating of the metal
enclosure can be minimized by the use of aluminum locknuts and by
cutting a slot between the individual holes through which the
Aluminum conduit, locknuts, and enclosures carry eddy currents, but
because aluminum is nonferrous, it doesn't heat up.
Editor's note: This information was extracted from Mike
the National Electrical Code
Fluke 117 Electrician's Multimeter with
Non-Contact voltage. Designed by electricians. Engineered by Fluke.
Compact true-rms meter for commercial applications. The Fluke 117 is
ideal meter for demanding settings like commercial buildings, hospitals
and schools. The 117 includes integrated non-contact voltage detection
to help get the job done faster. For
more information, click here.
What's Wrong Here?
By Joe Tedesco
Think you know how this installation violates the
NEC? Visit EC&M's
Web site to see the answer.
Hint: A case of the bends.
By Mike Holt
Q. What is the minimum service drop clearance
above a roof?
Visit EC&M's Web
site to see the answer.
By Steven Owen
Q. A construction site has 10 office trailers.
Each unit is identical. The HVAC unit for each trailer has a
load current of 27A and a branch circuit selection current of 30A at
208VAC, 3-phase. What is the proper size for the ground-fault,
short-circuit protective device for each HVAC unit?
Web site for the answer and explanation.
Streamline the implementation of your Arc Flash and Electrical Safety
Program. What used to take hours, now takes mere seconds! EasyPower
delivers Windows® -based tools for designing, analyzing,
and monitoring electrical power systems. Register now for the
EasyPower training coming to Orlando, Florida November 5 - 9, 2007!
One-touch automated design and one-touch automated protective device
coordination options, will also be introduced!
Code News Update
Comments Sought on Tentative Interim
According to August/September 2007 issue of NFPA
News, two Tentative Interim Amendments (TIAs) to the 2008 version
the National Electrical Code have been proposed to the NFPA. The
TIAs are now available for public review and comment. Any comments on
these TIAs should be filed with the Secretary Standards Council by
September 17, 2007. The NEC technical committee will consider all
comments prior to taking final action on these items. The Standards
Council will then review the technical committees' ballot results, the
public comments, and any other information that has been submitted to
determine whether to issue the TIA at its meeting October 3-4, 2007.
The two TIAs in question are as follows:
TIA Log No. 881 -- "Add the following Exception to Articles
374.17, 366.23(A)(B), 372.11, 372.17, 374.5, 374.17, 376.22, 378.22,
384.22, 386.22, 388.22, 392.9, 392.10, and 392.11: Exception No. 1:
Additional conductors shall not be added unless with a tested and
or recognized method or device that maintains spacing for air to
surround the conductors, and it is to be followed by its installation
instructions with its limitations. Article 310.15(B)(a) spacing shall
TIA Log No. 891 -- "Revise the following section to read as
follows: (374.17) The ampacity adjustment factors in Table
shall not apply to cellular metal floor raceways."
Cool Electronic Cabinets
Stop electronic control downtime due to heat, dirt and moisture. UL
Listed Cabinet Coolers from EXAIR produce 20 degree Fahrenheit air from
an ordinary supply of compressed air to cool electrical controls.
Thermostat control minimizes air usage. Maintains the NEMA 4, 4X
(stainless steel) and 12 rating of the enclosure. Web site offers
detailed information, downloadable drawings and PDF literature.
Shows and Events
EC&M Code Change
Where do you turn when you need accurate information on
changes to the National Electrical Code? Acknowledged as the leaders in
providing information on the NEC, EC&M magazine and EC&M
Seminars have been the preferred sources of this information for more
than 60 years. Seven Code change conferences have been scheduled in the
fall of 2007. Host cities include: Atlanta, Boston, Dallas, Orlando,
Philadelphia, St. Louis, and Seattle.
As an approved provider with the National Council of Examiners for
Engineering and Surveying (NCEES), through its Registered Continuing
Education provider Program (RCEPP), professional engineers attending
of our 2008 Code change conferences will receive Professional
Development Hours (PDHs), a requirement for re-licensing in many
The conferences are also approved by every state that has a continuing
education requirement for contractors and electricians.
For additional information on the dates and locations of these
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton Media, Inc. | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2013, Penton Media, Inc. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.