Conductors in Parallel
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code” and “NEC” refer to the
National Electrical Code®, which is a registered
trademark of the
National Fire Protection Association.
Top 50 NEC Rules
Conductors in Parallel
By Mike Holt
Ungrounded and grounded neutral conductors sized 1/0
and larger can be connected in parallel (i.e., electrically joined at
When conductors are run in parallel, the current must be evenly
distributed between the individual parallel conductors. This is
accomplished by ensuring that all ungrounded and grounded neutral
conductors within a parallel set are identical. Each conductor of a
parallel set must:
In addition, raceways or cables containing parallel conductors must
the same physical characteristics and the same number of conductors in
each raceway or cable. Conductors for one phase (ungrounded conductor)
or the grounded neutral conductor, aren't required to have the same
physical characteristics as those of another phase or grounded neutral
conductor to achieve balance.
- Be the same length.
- Be made of the same conductor material (copper/aluminum).
- Be the same size in circular mil area (minimum 1/0 AWG).
- Use the same insulation material (like THHN).
- Terminate in the same method (set screw versus
The equipment grounding (bonding) conductors for circuits in
must be identical to each other in length, material, size, insulation,
and termination. In addition, each raceway (where required) must have
equipment grounding (bonding) conductor sized in accordance with
250.122. The minimum 1/0 AWG rule of 310.4 doesn't apply to equipment
grounding (bonding) conductors [250.122(F)(1)].
When more than three current-carrying conductors are run together in
a raceway longer than 24 inches, the ampacity adjustment factors of
Table 310.15(B)(2)(a) must be applied. See 310.10 and 310.15 for
Editor's note: This information was extracted from Mike
the National Electrical Code
No matter where you are in the challenging process of developing or
implementing an Arc Flash Safety Program, you can rely on ESA to help.
Take advantage of the free resources we offer such as our Arc Flash
Book, Arc Flash Specification, 10 Steps of an Effective Arc Flash
Safety Program guide and more. www.easypower.com/support.php
What's Wrong Here?
By Joe Tedesco
Think you know how this installation violates the
NEC? Visit EC&M's
Web site to see the answer.
Hint: Think Too-Tall Jones
By Mike Holt
Q. When are insulated bushings required on
Visit EC&M's Web
site to see the answer.
By Steven Owen
Q. A cable tray system has been installed to
support service entrance conductors. The service entrance conductors
consist of six sets of three-conductor 500kcmil interlocked armored
cables installed in parallel in a single layer in the tray. An
additional feeder, consisting of three sets of parallel three-conductor
500kcmil interlocked armored cables, has been installed in a single
layer in the same cable tray. The cable tray is wide open (i.e., no
barriers or dividers). Is this installation NEC compliant?
- Yes, because all cables are interlocked armored cables.
- No, because conductors other than service entrance conductors are
not permitted in the same cable tray with service entrance conductors,
unless a solid fixed barrier of a material compatible with the cable
tray is installed to separate the service entrance conductors from the
- No, because interlocked armored cables are not permitted to be used
as service entrance conductors.
- No, because cable trays cannot be used to support service entrance
Web site for the answer and explanation.
Cool Electronic Cabinets
Stop electronic control downtime due to heat, dirt and moisture. UL
Listed Cabinet Coolers from EXAIR produce 20 degree Fahrenheit air from
an ordinary supply of compressed air to cool electrical controls.
Thermostat control minimizes air usage. Maintains the NEMA 4, 4X
(stainless steel) and 12 rating of the enclosure. Web site offers
detailed information, downloadable drawings and PDF literature.
Shows and Events
EC&M Code Change
Where do you turn when you need accurate information on
changes to the National Electrical Code? Acknowledged as the leaders in
providing information on the NEC, EC&M magazine and EC&M
Seminars have been the preferred sources of this information for more
than 60 years. Seven Code change conferences have been scheduled in the
fall of 2007. Host cities include: Atlanta, Boston, Dallas, Orlando,
Philadelphia, St. Louis, and Seattle.
As an approved provider with the National Council of Examiners for
Engineering and Surveying (NCEES), through its Registered Continuing
Education provider Program (RCEPP), professional engineers attending
of our 2008 Code change conferences will receive Professional
Development Hours (PDHs), a requirement for re-licensing in many
The conferences are also approved by every state that has a continuing
education requirement for contractors and electricians.
For additional information on the dates and locations of these
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton Media, Inc. | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2013, Penton Media, Inc. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.