Receptacles in Damp or Wet Locations
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code" and "NEC" refer to the
National Electrical Code®, which is a registered
trademark of the National Fire Protection Association.
Top 2008 Code Changes
Receptacles in Damp or Wet Locations
By Mike Holt
Receptacles installed in wet locations are now required
to be weather resistant.
As per 406.8(B)(1) Receptacles in Wet Locations, all 15A and 20A
receptacles installed in a wet location shall be within an enclosure
that is weatherproof when an attachment plug is inserted and all
non-locking 15A and 20A, 125V and 250V receptacles in a wet location
shall be listed as weather resistant. An exception notes that
receptacles subject to routine high-pressure washing spray may have an
enclosure that is weatherproof when the attachment plug is removed.
Wet locations are those subject to saturation with water, and
unprotected locations exposed to weather [Art. 100].
Exposed plastic surface material of weather-resistant receptacles
must have UV resistance to ensure deterioration from sunlight does not
take place or is minimal. In testing, receptacles are subjected to
temperature cycling from very cold to very warm conditions and then
additional dielectric testing. The rapid transition from the cold to
warm temperature will change the relative humidity and moisture content
on the device and the dielectric test ensures that this will not
a breakdown of the device's insulation properties.
The change to this subsection was made in response to concerns that
receptacles located outdoors are not always protected from detrimental
conditions such as low temperatures, exposure to ultraviolet radiation
(UV), physical damage, etc., and that weatherproof covers and
do not always provide sufficient protection from the elements.
The new exception allows receptacle covers in high-pressure spray
washing areas to be of the type that is weatherproof when the
plug is removed. When a weatherproof while-in-use cover is used with
high-pressure spray cleaning, liquid can spray into the enclosure
through the cable openings. This change allows the use of a snap cover
that does not have a cable opening in it while closed.
Demanding professionals need our
best DMM. The 289 True-rms Logging
Multimeter with TrendCapture was designed for those of you at the top
of your field.
Large 50,000 count, 1/4 VGA display Logging function with
expanded memory TrendCapture graphically review logged on data
Low Pass filter for adjustable speed drives
click here for more
What's Wrong Here?
By Joe Tedesco
Think you know how this installation violates the
NEC? Visit EC&M's
Web site to see the answer.
Hint: A case of overexposure
By Mike Holt
Q. We had a new swimming pool installed at our
house, and the electricians ran a cable to the pool equipment room
panel. Is this legal?
Visit EC&M's Web
site to see the answer.
By Steven Owen
Fill in the blanks.
When installing temporary wiring in exhibition halls, for events such
trade shows, the temporary wiring is __________ to be installed in
accordance with Art. 590. Flexible cables and cords approved for hard
extra-hard usage __________ permitted to be laid directly on the floors
where protected from contact by the general public. Ground-fault
circuit-interrupter protection __________ required.
- required / are not / is
- mandatory / are not / is
- permitted / are / is not
Web site for the answer and explanation.
Escape the cold weather! Join us for
EasyPower training in Orlando, Florida, January 12 - 16, 2009.
Streamline the implementation of your Arc Flash and Electrical
Safety Program. Experience the fastest, most accurate
Windows®-based tools for designing, analyzing, and
electrical power systems. This seminar fills up quickly; download a
brochure and register by December 29th! http://www.easypower.com/support_training.php
Watch EasyPower in action through our online videos: http://www.easypower.com/videos.php
Code News Update
Preparing for Action
NFPA documents are presented for action at the
association's annual technical meeting only when amending motions have
been submitted to the NFPA in advance of the meeting and certified by
the Motions Committee of the Standards Council. Under the rules in
effect, only Certified Amending Motions and proper Follow-Up Motions
will be allowed.
The following documents in the Annual 2009 Revision Cycle that could
receive Notice of Intent to Make a Motion and be presented for action
the 2009 Association Technical Meeting in Chicago include:
The Motions Committee Report on documents in the 2009 revision cycle
will be posted on the NFPA Web site no later than May 1, 2009.
- NFPA 110, Standard for Emergency and Standby Power Systems
- NFPA 111, Standard on Stored Electrical Energy Emergency and
Stop electronic control downtime due to heat, dirt and moisture. UL
Listed Cabinet Coolers® from EXAIR produce 20 degree
from an ordinary supply of compressed air to cool electrical controls.
Thermostat control minimizes air usage. Maintains the NEMA 4, 4X
(stainless steel) and 12 rating of the enclosure. Web site offers
detailed information, downloadable drawings and PDF literature. click here for more
Shows and Events
The Electric West Show, to be held March 18-20, 2009 at
the Las Vegas Convention Center in conjunction with the Power Quality
Reliability Conference, is the perfect place to brush up on the latest
NEC topics – and earn continuing education credits in the process.
Geared toward electrical contractors, consulting & specifying
electricians, and plant facility personnel, there’s something for
everyone at the Electric Show. The biggest electrical marketplace in
western United States, this event attracts 250 exhibiting companies and
more than 6,000 attendees every year. Here's a preview of some of the
NEC seminars planned for next year's event:
For more information, visit our Web
- One- and Two-Family Dwelling Unit Electrical Systems
- Changes to the 2008 NEC
- Swimming Pools and Similar Installations (NEC Article 680)
- Introduction to the 2009 NFPA 70E
Eliminate Red Tags
It takes more than the UL
Mark on a product to satisfy code requirements. Before your next
installation, use UL's Code Compliance Database to identify the
correlation between model codes and UL Certified products, as well as
find manufacturers of certified products.
Click here today
find up-to-date UL Listed products at the UL Code Correlation
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2014, Penton. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.