Tamper-Resistant Receptacles in Dwelling Units
Comments Sought on
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code" and "NEC" refer to the
National Electrical Code®, which is a registered
trademark of the National Fire Protection Association.
Top 2008 Code Changes
406.11 Tamper-Resistant Receptacles
By Mike Holt
Requirements for tamper-resistant receptacles were
to the 2008 NEC. The new requirement states that all 15A and 20A, 125V
receptacles in dwelling units shall be listed as tamper resistant.
This rule applies to receptacles installed behind appliances, above
countertops, and other locations out of the reach of children.
Demanding professionals need our
best DMM. The 289 True-rms Logging
Multimeter with TrendCapture was designed for those of you at the top
of your field.
Large 50,000 count, 1/4 VGA display Logging function with
expanded memory TrendCapture graphically review logged on data
Low Pass filter for adjustable speed drives
click here for more
What's Wrong Here?
By Joe Tedesco
Think you know how this installation violates the
Web site to see the answer.
Hint: Proper termination?
By Mike Holt
Q. Can a junction box contain both 277V and 120V
Visit EC&M's Web
site to see the answer.
By Steven Owen
With respect to fixed stage equipment other than
switchboards, what is the maximum ampere load permitted on a 20A branch
circuit serving floodlights, border lights, and proscenium
- 20A or 100%
- 16A or 80%, as per 210.20(A)
- 10A or 50%, as per 210.23(A)(2)
Web site for the answer and explanation.
Escape the cold weather! Join us for
training in Orlando, Florida, January 12-16, 2009. Streamline
the implementation of your Arc Flash and Electrical Safety Program.
Experience the fastest, most accurate Windows®-based
tools for designing, analyzing, and monitoring electrical power
This seminar fills up quickly; download a brochure and register by
December 29th! http://www.easypower.com/support_training.php
Watch EasyPower in action through our online videos: http://www.easypower.com/videos.php
Code News Update
Comments Sought on Proposed
As published in the December issue of NFPA News,
the following Tentative Interim Amendment (TIA) has been proposed to
NFPA 70-2008, National Electrical Code
TIA Log No. 936
Submitter: Wayne H. Robinson, Lothian, Md.
1. Revise 680.26(B)(1)(b)(2) as follows: "Conform to the contour of the
and the pool deck and the perimeter surfaces outlined in
2. Revise 680.26(B)(2)(b) as follows: "Alternate Means. Where
structural reinforcing steel is not available or is encapsulated in a
non-conductive compound, a copper grid
conductor(s) shall be
utilized where the following requirements are met:
(1) At least one minimum 8 AWG bare solid copper conductor shall be
(2) The conductors shall follow the contour of the perimeter
(1) The copper grid shall be constructed of 8 AWG bare copper and be
arranged meeting the requirements of 680.26(B)(1)(b)(3).
(2) The copper grid shall follow the contour of the perimeter
extending (3 ft) horizontally beyond the inside walls of the
(3) Only listed splices shall be permitted.
(4) The required conductor shall be 450 to 600 mm (18 to 24 in.)
the inside walls of the pool.
(5) The required conductor shall be secured within or under the
perimeter surface 100 mm to 150 mm (4 in. to 6 in.) below the
(4) Be secured within or under the deck or unpaved surfaces no more
than 150-mm (4 in. to 6 in.) from the underside of the deck."
To review the submitter's reason and emergency nature text for this
here and scroll down to the bottom of page 2.
This TIA has been published for public review and comment. Comments
should be filed with the Secretary, Standards Council by January 16,
2009. You should identify the TIA number when submitting your comments.
The Standards Council will review the technical committees' ballot
results, the public comments, and any other information that has been
submitted when it considers the issuance of the TIA at its March 3-4,
EXAIR's low cost Cabinet Coolers® stop electronic
due to heat, dirt and moisture. UL Listed Cabinet Coolers produce 20
degree Fahrenheit air from an ordinary supply of compressed air to cool
electrical controls. Thermostat control minimizes air usage. Maintains
the NEMA 4, 4X (stainless steel) and 12 rating of the enclosure. Web
site offers detailed information, downloadable drawings and PDF
literature. click here
Shows and Events
The Electric West Show, to be held March 18-20, 2009 at
the Las Vegas Convention Center in conjunction with the Power Quality
Reliability Conference, is the perfect place to brush up on the latest
NEC topics -- and earn continuing education credits in the process.
Geared toward electrical contractors, consulting & specifying
electricians, and plant facility personnel, there's something for
everyone at the Electric Show. The biggest electrical marketplace in
western United States, this event attracts 250 exhibiting companies and
more than 6,000 attendees every year. Here's a preview of some of the
NEC seminars planned for next year's event:
For more information, visit our Web
- One- and Two-Family Dwelling Unit Electrical Systems
- Changes to the 2008 NEC
- Swimming Pools and Similar Installations (NEC Article 680)
- Introduction to the 2009 NFPA 70E
Eliminate Red Tags
It takes more than the UL
Mark on a product to satisfy code requirements. Before your next
installation, use UL's Code Compliance Database to identify the
correlation between model codes and UL Certified products, as well as
find manufacturers of certified products.
Click here today
find up-to-date UL Listed products at the UL Code Correlation
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2013, Penton. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.