Pending Code Change
Item for 2011 NEC
Calling All Code
About this Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
Let you know what could be changing in the Code®.
Help you brush up on your ability to apply the
Test your knowledge of the Code® with a Q&A format.
Provide information on upcoming Code® seminars and
Give you an opportunity to sound off on
We want to make sure we're providing you with the content you need to
better manage your business or enhance your technical skills. E-mail us and let us know
what you want to see in future issues of this e-newsletter. We will do
our best to address your request in a future issue of CodeWatch.
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the
CodeWatch archive on EC&M's Web site.|
Tell a friend about CodeWatch
Do you know
of someone who'd like to receive CodeWatch? Visit the subscriber site, enter
their e-mail address and spread the wealth!|
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code" and "NEC" refer to the
National Electrical Code®, which is a registered
trademark of the National Fire Protection Association.
Pending Code Change Item for 2011
As noted in the NEC Committee Report on
Proposals, 2010 Annual Revision Cycle, Code-Making Panel 17 has
voted to accept a Code change submitted by Gary L. Siggins,
Laboratories, Inc. (Log #2357 NEC-P17). The recommendation calls for
revising the text of 680.2 as follows:
"Dry-Niche Luminaire. A luminaire intended for installation
the floor or wall of a pool, spa, or fountain in a niche
that is sealed against the entry of
As noted in the substantiation summary, this change will clarify
new luminaire designs can also be used in floor mounting applications
and in spas. This change also supports deletion of the word "pool" from
the summary text, as their application is now more widespread.
You can download
an electronic version of the report via the NFPA Web site.
Although the comment period is now closed, the results of the
committee action on all submitted comments will be published in the
NEC Committee Report on Comments, which will be made available
all who request it. The Report on Comments mail date is
for March 29, 2010.
Imagine the possibilities
What would you do if you
could be in two places at once?
The NEW Fluke 233 wireless
remote display digital multimeter with removable magnetic display
you to be 30ft away from the measurement point. Perfect for those
difficult measurements where display viewing is challenging. www.fluke.com/233_DMM
What's Wrong Here?
By Brian J. McPartland
Think you know how this installation violates the
Web site to see the answer.
Hint: Raceway-supported box
By Mike Holt
Q. I recently saw a service disconnect that was
being used as a conduit for two feeder circuits. Is this legal?
Visit EC&M's Web
site to see the answer.
By Steven Owen
A question has arisen related to the installation of a
new 112.5kVA dry-type transformer, which is equipped with ventilated
openings. The transformer will be located in an electrical equipment
room, directly across from a 480V switchboard. The rear of the
transformer will be pushed tight against a concrete wall. The distance
between the front of the transformer and the front of the switchboard
will be 48 in. Why was this proposed installation rejected by the
- It was turned down because a 112.5kVA dry-type transformer must be
installed in a vault or a room of fire-rated construction with a 3-hour
- It was turned down because the distance between the transformer and
the switchboard should have been 60 in.
- It was turned down because the transformer was pushed tight to the
concrete wall, which will reduce air flow needed to cool the
transformer, as required by the manufacturer and the NEC.
- The AHJ is wrong. There was no need to reject the installation as
is compliant with the requirements of the NEC.
Web site for the answer and explanation.
Cool Electronic Cabinets
Stop electronic control downtime due to heat, dirt and moisture. UL
Listed Cabinet Coolers from EXAIR produce 20 degree Fahrenheit air from
an ordinary supply of compressed air to cool electrical controls.
Thermostat control minimizes air usage. Maintains the NEMA 4, 4X
(stainless steel) and 12 rating of the enclosure. Web site offers
detailed information, downloadable drawings and PDF literature.
Click here for more
Code News Update
Calling All Code Writers
Don't miss an opportunity to help create the next
edition of NFPA 70E, Standard for Electrical Safety in the Workplace.
Time is running out! You have between now and Jan. 5, 2010 to submit
your proposals for new requirements, revisions to existing
or deletion of existing requirements. But don't just fly by the seat of
your pants and submit a poorly worded submission without any technical
justification. It's important that you draft your proposal in a clear
and simple manner and back it up with technical justification. You must
convince the Code committee members that your change makes sense for
You can download
a proposal form directly from the NFPA Web site.
Get more out of your business when it matters –
today. Make sure every penny you spend on your company counts.
Align with the industry leader. Get the tools and systems to make your
business take off today. Discounts and rebates on supplies, support and
training from the best in the industry. Get the Mr. Electric Advantage.
Shows and Events
The Electric West Show, to be held March 16-18, 2009 at
the Las Vegas Convention Center, is the perfect place to brush up on
latest NEC topics — and earn continuing education credits in the
process. Geared toward electrical contractors, consulting & specifying
engineers, electricians, and plant facility personnel, the conference
program will offer the following NEC seminars, presented by industry
experts such as Mike Holt, Keith Lofland, and Edward Gorginian.
For more information, visit our Web
site, or click here
- Analysis of 2011 NEC Changes
- Understanding Important NEC Requirements
- Dwelling Calculations
- Advanced NEC Calculations
- Grounding vs. Bonding
- Swimming Pools and Similar Installations
Have a UL White Book but not sure how to use
Discover why the UL White Book is Part 2 of the NEC
and how it will help you avoid "Red Tagged" jobs. Click here to learn how
to use the White Book FREE online or to order a copy.
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton Media, Inc. | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2013, Penton Media, Inc. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.