Making Motor Repairs Stick
NEC in the Facility
About This Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
MRO Insider addresses topics such
Working with management and supervision
National Electrical Code® on the production floor
Safety procedures and programs
Equipment maintenance and testing tips
Managing motors and generators
Trends in training and education
Managing energy use
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the MRO
Insider archive page on the EC&M Web site.|
Share with a Friend
Do you know
someone who'd like to receive his or her own copy of MRO Insider? Visit
the subscriber site enter their e-mail address, and spread the wealth.
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code" and "NEC" refer to the
National Electrical Code®, which is a registered
trademark of the National Fire Protection Association.
How well do you maintain your equipment grounding
conductors (EGCs)? Do you maintain them at all? If so, then how?
First, it helps to get the terminology correct. The EGC has nothing
to do with grounding. In fact, it's pointless to ground load side
equipment. With the 2008 revision, the NEC made great strides toward
correcting misuse of the word "grounding." But it still has to cross
finish line on that problem; thus, it prescribes "grounding" conductors
that don't do grounding.
The Art. 100 definitions of "grounding" and "bonding" cut through
confusion. Based on those definitions, an EGC isn't a grounding
(connect to earth) conductor. The EGC is a bonding conductor. As
such, it forms a low-resistance metallic path.
To read more on this story, visit EC&M's Web
AMAXX® by MENNEKES
One AMAXX unit
replaces multiple receptacle installations, saving you labor, material
Offered in single gang to five-gang models, AMAXX provides configurable
flexibility for receptacles
and switches in an innovative enclosure system. With AMAXX, you can
customize quickly, safely and easily.
Call 1-800-882-8110 or visit us online at www.goMENNEKES.com.
A critical 75-hp motor has failed three times in as
years. Each time has been preceded by a loud rattling and excessive
shaking that lasted a few minutes. After the second time, you switched
to a different manufacturer. This third failure has you on the hot
Should you try a third manufacturer, or should you do something else?
Web site to see the answer.
To make a motor repair stick, follow these three
- Before bringing the motor to the installation area, manually turn
the rotor. It should turn freely and noiselessly. Nobody likes to take
hr to install a motor only to yank it back out again due to a bent
- Before connecting motor leads, conduct insulation resistance tests
on its windings. This dries condensation from the windings before
applying full current, and it provides baseline maintenance data.
- Before connecting the motor to its load, PM the load or at least
check it (e.g., check gearbox oil).
Stainless Steel Liquid Tight
ElecDirect’s line of Stainless Steel
Liquid-Tight Conduit Connectors are made of corrosion resistant 304
stainless steel and designed specifically for flexible liquid tight
conduit. Ideal for highly corrosive environments, these connectors are
extremely durable and UV resistant. They also include an insulated
throat for further cable protection.
Starting from only $19.99 —
it’s time to stop replacing broken plastic and rusted steel
— or call toll free 800-701-0975 for more information.
NEC in the
Exactly how you can classify a location depends on the
properties of the ignitable fibers or flyings that may be present and
their concentration [506.5].
- Summary of Zone 20 definition: Ignitable fibers or flyings are
consistently present and are present for long periods [506.5(B)(1)].
- Summary of Zone 21 definition: Ignitable fibers or flyings are
likely to exist under normal operations, during repair, or during
- Summary of Zone 22 definition: Ignitable fibers or flyings are
not likely to exist under normal operations
Fall protection includes nets and safety harnesses,
which serve to arrest a fall rather than prevent it. Before working on
any elevation, assess the fall protection needs. Choose the personal
protective equipment (PPE) that is most appropriate for that particular
location and the work you're doing.
To read more on this story, visit EC&M's Web
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2014, Penton. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.