Testing, Part 2
NEC in the Facility
About This Newsletter
e-newsletter is brought to you from the
publisher of EC&M magazine.
MRO Insider addresses topics such
Working with management and supervision
National Electrical Code® on the production floor
Safety procedures and programs
Equipment maintenance and testing tips
Managing motors and generators
Trends in training and education
Managing energy use
To unsubscribe from this newsletter go to: Unsubscribe|
To subscribe to this newsletter, go to: Subscribe
To get this newsletter in a different format (Text or HTML),
or to change your e-mail address, please visit your profile
page to change your delivery preferences.
issue? Visit the MRO
Insider archive page on the EC&M Web site.|
Share with a Friend
Do you know
someone who'd like to receive his or her own copy of MRO Insider? Visit
the subscriber site enter their e-mail address, and spread the wealth.
To find out
how to advertise in this newsletter, e-mail David Miller or call him at
The designations "National Electrical Code" and "NEC" refer to the
National Electrical Code®, which is a registered
trademark of the National Fire Protection Association.
Resistance Testing, Part 2
Insulation resistance testers measure these three
- Absorption current starts high and then drops. At the same
time, voltage starts low and rises. What you're measuring is the rate
storage (absorption) of potential energy in and on insulation.
Understanding this process is important to understanding the time
resistance method of insulation testing.
- Capacitive current is the initial surge of current that
occurs when you apply voltage to a conductor. The conductor acts like a
capacitor in that it "charges up." As with absorption current,
capacitive current starts high and then drops.
- Leakage current, also called "conduction current," is the
steady flow of current through and on the insulation. If you graph this
on a time trend, you should notice a gradual sloping of the line. When
that slope suddenly changes, the insulation is undergoing accelerated
Imagine the possibilities and win a multimeter.
New Fluke 233 Remote Display Digital Multimeter allows you to be in two
places at once. The removable magnetic display allows you to be 30 feet
away from the measurement point. Tell us how it will expand your
capabilities and be entered to win a free 233 Meter. www.fluke.com/imagine_the_possibilities
A rash of motor failures has afflicted your plant. Your
plant engineer read some application notes from the Web site of a test
instrument manufacturer and subsequently used a power analyzer on the
feeders of these motors. There were some anomalies, but nothing that
explains these failures.
These failures are occurring in a few unrelated systems: the plant
HVAC, a process exhaust hood, a scrap grinder, a conveyor system, and a
wash tank. These same systems keep having motor failures. What should
you look at to get to the bottom of this problem?
Visit EC&M's Web
site to see the answer.
A repair that isn't done correctly is a failure waiting
to happen. Some common errors include:
You can prevent most "failed repair" problems by addressing potential
failure causes in your repair procedures. Ask a few key questions, such
as: For breaker X, what lubricants do we use? For feeder bus 06E, which
Belleville washers do we use?
- Poor hygiene. Lay disassembled parts on a clean surface,
as cloth for that purpose. At every step, prevent the introduction of
grit, chemical contaminants, and water. Even finger oil on contact
surfaces can create problems later.
- Misapplication of lubricants. No, it's not okay to spray
breakers with a handy can of spray lubricant. A spray lubricant doesn't
have the "body" to adhere to high pressure points of contact. Use only
the lubricant specified by the manufacturer. Don't over lubricate.
- Re-using old fasteners. For control wiring and other
low-torque applications, this is usually acceptable. If you need more
than a screwdriver to tighten the connection, replace the hardware.
- Misapplication of spring-type fasteners. Belleville washers
are commonly misapplied. The errors are usually over-tightening or use
of the wrong size. Replace after each use with the correct size, and
follow the installation instructions for a reliable connection.
- Improper torqueing. Improper tightening of motor mounting
bolts is a leading cause of replacement motor vibration problems. Use
the torque value specified for the fasteners you’re using, not the
value from a generic table.
How safe are you? Ferraz Shawmut makes it easy to test
your knowledge of electrical protection with its innovative Protection
Intelligence Quotient (PIQ) Quiz. Visit http://us.ferrazshawmut.com/PIQECM,
take the quiz and enter to win a $100 gift card. Three winners are
selected every month. Turn to Ferraz Shawmut for the products and
knowledge to be a real protection pro!
NEC in the
Most facilities today have surge arresters on the
building supply (service). These are typically bought on a budget
mentality that results in a waste of the entire investment. It doesn't
have to be that way. In fact, correct specification and installation
will provide a very high return on investment (ROI).
The first thing to consider is that these systems need to be part of
a larger surge protection strategy. They will protect only against the
larger spikes (reducing them to a lower voltage) from outside your
To read more on this story, visit EC&M's Web
The best protection against arc blast is "don’t be
there." This, however, isn't always possible. The next best precaution
is to minimize your exposure (do as much as possible outside the
hazardous area) and wear the proper PPE.
You may need to wear protective sleeves, a blast suit, or other
protective clothing. Don't fall into the trap of asking, "What can I
by with?" Instead, ask what you must do to protect yourself against the
highest energy hazard available in this location.
- Thoroughly assess the situation before making PPE decisions.
- Avoid "calculation obsession." Protection calculations determine
minimum protection. You aren't required to downgrade protection
to fit those calculations.
- Remember that there is always enough time to perform the proper
safety analysis prior to commencing work. You may not get a second
You are subscribed to this newsletter as #email#
For questions concerning delivery of this newsletter, please contact
Customer Service Department at:
Customer Service Department
A Penton Media publication
US Toll Free: 866-505-7173
Penton | 1166 Avenue of the Americas, 10th Floor | New York, NY 10036
Copyright 2014, Penton. All rights reserved. This article is
protected by United States copyright and other intellectual property
laws and may not be reproduced, rewritten, distributed,
displayed, published or broadcast, directly or indirectly, in any
without the prior written permission of Penton Media, Inc.